AQ01 to AQ101 and AQ101 to AQ110 Distances
Maximum distance between AQ110/AQ101 and AQ01 is 200m.
Maximum distance between AQ110 and AQ101 is 1000m.
Maximum distance between AQ110 and AQ110 is 1000m.
AQ-300 series relays protection and communication separation on CPUs
AQ-300 series units have one CPU module with two processors on the PCB: RDSP, which is responsible for the sampling and for the protection, automation and control functions CDSP, which is responsible for the communication. In special cases there can ...
Load report file from the AQ-300 IED for faster technical support
In case of having technical issues with AQ-300 series IED it is advised to load a “report file” from the relay to help Arcteq Relays to determine the cause for the issue faster. The report file may contain information valuable for the manufacturer. ...
Downloading AQtivate 200 setting tool
To download AQtivate 200 setting tool visit our website https://arcteq.fi/ and log in to our website. Once logged in you should find download link for AQtivate 200 installer at https://arcteq.fi/downloads/ To get full use of the features included in ...
AQ-200 series power supply connection
AQ-200 series IEDs have two different types of voltage supplies available. Type H = 80...265 VAC / VDC Type L = 18...72 VDC The power supply type is indicated in the hardware configuration. The type can be checked from the serial number sticker or ...
About AQ-200 series units and RSTP.
AQ-200 series devices don’t implement any support for the RSTP-protocol. They should be always treated as non-RSTP devices. That being said, under certain circumstances, it is possible to mix RSTP and non-RSTP devices. For example, the so-called ...