Change setting groups manually to ease commissioning tests
Sometimes testing the
protection functions in each setting group can be laborious if changing the
settings group activation requires a very specific condition. To work around
this it is possible to temporarily change the setting group manually by
enabling Force SG change and then
choose the desired setting group with Force
SG. If Live Mode-is activated, active setting group is displayed in Active setting group.