Switching between setting groups manually
Sometimes testing the
protection functions in each setting group can get very time consuming if switching between the setting groups requires a very difficult to achieve condition. In these cases it is possible to temporarily change the setting group manually by
enabling Force SG change and then
choose the desired setting group with Force
SG. If Live Mode-is activated, active setting group is displayed in Active setting group.
Change setting groups manually to ease commissioning tests
Sometimes testing the protection functions in each setting group can be laborious if changing the settings group activation requires a very specific condition. To work around this it is possible to temporarily change the setting group manually by ...
Setting thermal capacity manually when testing line/machine/transformer thermal overload protection
When testing thermal overload protection functions resetting the thermal capacity it often needed so that the test can be repeated multiple times without having to wait for the thermal cap to got down. This can be done with parameter Cold reset theta ...
Disturbance recorder setting recommendations
Disturbance recorder can be extremely helpful in analyzing the reason for protection function trips. Disturbance recordings use standard COMTRADE file format. This means the recording files can be opened by any software that supports COMTRADE format. ...
Downloading AQtivate 200 setting tool
To download AQtivate 200 setting tool visit our website https://arcteq.fi/ and log in to our website. Once logged in you should find download link for AQtivate 200 installer at https://arcteq.fi/downloads/ To get full use of the features included in ...
Windows systems supported by AQtivate setting tool
AQtivate setting tool for AQ-200 series IEDs supports any version of Windows 7, 8 and 10. Other operating systems might be able to launch the software but we can't guarantee good performance.